Our client had a very large wet dust collector sited outdoors which pulled air from 3 booths in which titanium grinding took place. Titanium dust is explosive hence the requirement for a wet dust collector, where the sparkrisk is mitigated immediately as it hits the water. As an environmentally aware […]
It is possible to catch COVID-19 either by breathing in droplets coughed out or exhaled by a person with COVID-19 or by touching eyes, nose or mouth after handling a contaminated object. All sections of society, including businesses and employees must play a role if we are to stop the spread of this disease. Compliance […]
Our client had a single large metal dressing booth. The dust collector was highly energy inefficient, we wrote a business case and carried out energy saving calculations to prove a less than 5 year ROI. This system was also a single point of failure in a critical process line. Following Lean excercises with our in-house […]
A firing range where the contaminent was lead dust and unburnt propellant. failed its insurance inspections. They contacted Compliance LEV to assess the system. We found that there was more air being pushed into the range than was being drawn out, this meant that the room became charged with a positive pressure and […]
Sending all the key workers keeping this country running very kind thoughts and a wish for you all to stay safe and well. Thank you from all Compliance LEV and their families. (Happy times before lock down)
We are often approached by new clients where the client has new equipment or processes and are not sure if LEV is required and if it is, what type. At Compliance LEV we are always happy to talk things through with existing and new clients and even carry out a site visit if required. COSHH […]
Compliance LEV designed a chemical LEV system to handle hydroxide flake for a Rip and Tip process. This is a full stainless steel dust collector installed and commissioned by Compliance LEV in one day.
Two new wall hung LEV systems with 3 meter manipulating arms for our bioethanol client. These system can cope with high levels of dust and fume, and are spark minimised. These are non explosive, recirculating systems.
New employee, Garry Simmonds installing a bakery process flour dust LEV system for a client in Leeds. Stainless steel food grade local exhaust ventilation system, delivered installed and commissioned in one day.